BOILER & PRESSURE VESSEL REGISTRATION
1. This circular details the requirements for the registration of boilers and pressure vessels for use in British Columbia. Boilers and pressure vessels shall be registered in accordance with CSA B51 “Boiler, Pressure Vessel and Pressure Piping Code.” Registration submissions must be sent to the attention of Design Survey, Engineering & Research, Operations. 2. The standards governing the design and construction of boilers and pressure vessels are the ASME Boiler and Pressure Vessel Codes except as otherwise detailed in CSA B51. Sufficient documentation to verify that the design conforms to the applicable ASME code shall be submitted. As a minimum, the following information and documentation shall be submitted: (a) (b) (c) (d) A completed British Columbia CRN application form Design data such as ASME code specification, material specifications, pressure ratings, temperature ratings and type of service Drawings showing dimensions, construction and welding details of the proposed vessel design ASME code calculations
3. The drawings shall be identified by number and revision and indicate ASME code of construction (edition and addenda), non-destructive examination requirements, maximum allowable working pressure, minimum and maximum design temperatures, service fluid specific gravity, heat treatment, impact testing, corrosion allowance, nozzle locations, reinforcement and dimensions, flange and fitting standards, ASME material specifications, bill of material and nameplate facsimile. All design details and material specifications referenced in the calculations shall be included in the drawing. Conditions such as seismic or wind loadings, which may limit the vessel’s location must be detailed on the drawing. 4. Design calculations shall be to the latest ASME Code edition and addenda unless the submission details the reasons for using an earlier edition or addenda. The calculations shall contain sufficient information to verify that all applicable requirements of the specified ASME code have been complied with. If exemptions from specific code requirements are utilized in the design, the specific code section and subsection permitting the exemption must be identified and supported by an explanation or reason detailing how the exemption applies to the design. The calculations shall show the formulas used and reference the appropriate code section. Where the ASME code does not cover all details of the vessel design and construction, the submission must provide details utilizing recognized engineering practices or proof test results to show that the design method is as safe as those of the applicable ASME code. All UG-22 loadings must be considered in the design and, as a minimum, the submission must have a statement that all UG-22 loadings have been considered. Vessels with an overall length of 20 feet or more must have detailed seismic and support loading calculations. The calculations shall be signed by the person responsible for that function in the manufacturer’s quality control manual. The calculation package shall be numbered and have a method for revision control. 5. The registration submission will be reviewed to verify that all applicable code requirements have been considered in the design and the calculations made. Upon satisfactory review of the registration documentation, the vessel design shall be assigned a Canadian Registration Number (CRN). A stamped design registration letter indicating the CRN, date of registration, manufacturer’s name, description of the vessel, drawing numbers, registration fee and any other pertinent information will be sent to the applicant. A separate invoice will be forwarded for the registration fee. No other documents will be stamped or returned to the applicant. 6. Manufacturers of boilers and pressure vessels in countries other than Canada shall hold an ASME Certificate of Authorization and ensure that all boilers and pressure vessels are stamped with the appropriate ASME Code symbol and are registered with the National Board.
505 – SIXTH STREET, SUITE 200, NEW WESTMINSTER, BRITISH COLUMBIA, CANADA V3L 0E1 Phone: (778) 396-2027 Fax: (778) 396-2064 Website: www.safetyauthority.ca